Somtimes the most easy fix to a problem is the most overlooked and conserving power in the datacenter is perhaps no different. There are five easy and inexpensive ways for you to improve your datacenter's energy efficiency and reduce power consumption.
"These are easy fixes anyone can do that can save 10 percent to 15 percent on energy consumption in the first week," says Jim Smith, vice president of engineering for Digital Realty Trust, a datacenter design firm in Dallas.
1. The old hot-aisle, cold-aisle
Everyone knows that a hot-aisle, cold-aisle layout of computer equipment is the best method for assuring that a datacenter is properly cooled. In this layout, cool air flows through the aisles where it is taken in by the servers and other equipment and the heated air is exhausted out of the back of the system to the hot aisles and to the air conditioner return ducts.
Even though there is more to benefit to be received from hot-aisle, cold-aisle design than any other datacenter design issue, IT needs to watch for gear that exhausts air differently than out the back. You need ways for handling the hot exhaust from devices that are side- or top-ventilated. Cisco gear, for example, uses side ventilation; in Verari servers and blades and some HP gear, hot air is exhausted through the top of the equipment.
To maximize the hot-aisle, cold-aisle configuration, these devices should be placed in their own part of the datacenter where all exhaust air can be directed to a hot aisle or intermixed with rear-exhausting equipment and placed in a rack such as from Chatsworth that re-direct side-ventilated exhaust to the back of the cabinet.
Racks should also be positioned perpendicular to air conditioning to allow the unobstructed of heated air.
2. Ready, set, go airflow
Establish the right set points in configuring datacenter temperature and humidity. "Most people have the perception that the datacenter should be cold, says Smith.
"In reality, the datacenter should be slightly warm and slightly humid. If you look at the American Society of Heating, Refrigeration and Air Conditioning Engineers [ASHRAE] TC9.9, the mid-point of their range is 74 degrees and 50 percent humidity," says Smith.
That's the ideal environment for datacenter operation, says Smith.
"Many times you walk into datacenters and it's really cold. The extra energy required to get from the ASHRAE recommended set point down to 67 or 68 degrees; it's harder to get things colder," says Smith. "People also think a datacenter should be cool everywhere. It should only be cool on the intakes of the equipment. We constantly see people trying to cool air where heat is supposed to be."
The placement of temperature sensors on equipment and computational fluid dynamics studies can help IT determine correct setpoints for temperature/humidy levels. Most equipment is warranted to operate in temperatures up to as much as 95 degrees Fahrenheit. Temperature sensors are available from APC's NetBotz division.
Sun estimates that IT can reduce their energy costs by at least 4 percent for every upward setpoint change.