Ninety degrees is an unusually high temperature for a server room. Intel says in the report that it traditionally sets its chiller temperature to 68 degrees in its datacenters. Conventional wisdom dictates that air-side economization is better for mild, temperate climates, not regions where temperatures can hit the 80s, 90s, and beyond. There was method to Intel's seeming madness, however: "We reasoned that this might be feasible because server manufacturers specify that their products can operate in temperatures as high as 98 degrees."
Not content with simply pushing the temperature boundaries, Intel wanted to gauge how resilient the machines could be to humidity and air contaminants. To that end, Intel used no humidity controls whatsoever and installed just a standard household air filter "that removed only large particles from the incoming air but permitted fine dust to pass through."
Intel didn't go easy on its machines as it conducted this experiment. The chipmaker says that the servers were working at 90 percent utilization during the testing, crunching large production batch silicon design workloads.
As for the type of servers, Intel says they were standard, single-core, dual-socket, Intel-based machines that were roughly two years old. In other words, Intel didn't enlist specially hardened or ruggedized equipment but instead used the same type of machines found in the company's other datacenters.
During the 10-month test, Intel found that the machines cooled by outside air experienced humidity variations from four percent to more than 90 percent, and that it changed rapidly at times. Moreover, "the servers and the interior of the compartment became covered in a layer of dust."
Once the experiment was complete, Intel calculated that the air-economized trailer required 74 percent fewer KWh to keep cool then the air-conditioned trailer. Based on the testing, Intel concluded that in this particular region, at least, it could rely on air-side economizers 91 percent of the time and save $2.87 million on cooling at 10MW datacenter.
Cost savings aside, the other big question, of course, is how well did the server weather the unusually harsh conditions? After all, a datacenter full of fried or dust-clogged machines is pretty much worthless, no matter how inexpensive it is to cool. The answer: surprisingly well. "Despite the dust and variation in humidity and temperature, there was only a minimal difference between the 4.46 percent failure rate in the economizer compartment and the 3.83 percent failure rate in our main datacenter over the same period," Intel reports. "The failure rate in the trailer compartment with DX cooling was 2.45 percent, actually lower than in the main datacenter."